Fire rated cable is required in all life safety system installations, they are designed to maintain circuit integrity and continue to work for a specified period. To fully comply with the regulations Category 3 cable should be used for all smoke ventilation installations.
To celebrate turning 25 years old in 2017, SCS Group launched its own Fantasy Football League.
Over 38 weeks fantasy football managers fought it out to be top of the league, transferring players and rearranging teams each week. SCS Group offered prizes for those who were top of the league for the month, overall winner at Christmas and the top three winners overall.The League attracted managers from across the construction industry as well as staff from SCS Group, with a total of 112 people taking part.
SCS Group, of which Easivent is a part, will be sponsoring the Dronfield Town FC U18s kit for the next two seasons as part of its pledge to improve its engagement with the community.
The company has sponsored the same junior team several times as they have moved from U7s to U16s -both as SCS Group in the early days and most recently through its sales arm Easivent.
We’ll soon be rolling out our new EV-301 and EV-601 panels as an all singing and dancing replacement of the SP-300 and SP-600 panels.
You’ve installed our smoke/daily vent control panels, but did you know you can add on some features at little extra expense?
After 38 fabulous weeks of Premier League football we can now announce the winners of the SCS Group Fantasy Football League 2017/18.
Launched back in August, our League attracted managers from across the construction industry as well as staff from SCS Group, with a total of 112 people taking part.
A stairwell smoke ventilator is an automatic opening ventilator (AOV) which provides at least 1.0m2 of free area when open. It usually serves one of two purposes;
Stairwell ventilation can be achieved by automatically opening a window within the stairwell. As always this is subject to the minimum free area being achieved when calculated using the method in diagram C7 of Approved Document B.
It is recommended that bottom hinged outward opening windows are selected for efficient smoke evacuation, however this is not a requirement of ADB. Stairwell ventilators are more commonly used for replacing fresh air in a lobby extract system.
A variety of actuators are available for different window types depending on what the required free area is.